Sulzer Pump Service Reliability Tips
Capacity, Q, changes in direct proportion to the impeller diameter ratio, or the speed ratio.
Head, H, changes in direct proportion to the square of the impeller diameter ratio, or the square of speed ratio.
Power, P, changes in direct proportion to the cube of the impeller diameter ratio, or the cube of the speed ratio.
If you use impeller trim laws to calculate a new impeller diameter, the results are quite often different to what you expected:
1. The reason for this is that the Affinity laws are only valid under conditions of geometric similarity. When the diameter is trimmed the pump specific speed changes and the condition of similarity is violated.
2. Manufacturers quite often compensate for this by utilizing a compensation factor based on proprietary trim corrections.
3. Sulzer will be happy to help customers with these changes.
It must also be noted that when increasing speed, or impeller diameter, you need to check pump mechanical design limitations:
1. Is the motor/driver big enough?
2. Is the shaft strong enough, coupling, etc.
E10423 en 10.2016, Copyright © Sulzer Ltd 2016
This brochure is a general product presentation. It does not provide any warranty or guarantee of any kind. Please, contact us for a description of the warranties and guarantees offered with our products. Directions for use and safety will be given separately. All information herein is subject to change without notice.